Making wet waste destruction a sustainable reality
Irish environmental company SCFI was supported by the European Union’s Eco-Innovation initiative in a project to build a portable unit to demonstrate its innovative AquaCritox® wet waste treatment technology.
SCFI Group Ltd
Viewed : 1625
This White Paper describes the science behind hydrothermal oxidation (HTO) as a waste treatment methodology and its potential across a range of industrial applications, which is now, thanks to this project, a demonstrable reality.
AquaCritox and hydrothermal oxidation
AquaCritox is a hydrothermal oxidation process that involves the use of pressure, temperature and oxygen to effect partial or complete oxidation of the oxidisable components present in a sludge or contaminated water based waste stream. AquaCritox provides a single-step solution to the treatment of wet wastes such as sewage, drinking water, spent caustic and industrial organic aqueous waste streams. The technology delivers over 99.99% destruction of sludge – a far greater rate than other competing technologies, is also safe and odourless, and does not generate any hazardous emissions or by-products.
Typically, the process operates at minimum pressure of 165 bar and up to 240 bar. The use of such pressures is necessary to ensure that the water within the feedstock will remain in the near critical or super critical phase during the oxidation reaction. The use of high pressure also greatly increases the oxygen transfer rate which is often a limiting factor in lower pressure systems. This pressure is achieved and maintained by using high pressure feed pumps and a novel pressure control and let-down system.
The oxidation reaction is also temperature dependent. At low temperature it is unlikely to proceed or if so, will only occur at a very slow reaction rate. It is well known that reaction rates increase with temperature and in all chemical reactions it is necessary for the system to reach its activation energy whereby sufficient thermal energy is provided to break the bonds between atoms within molecules. Reactions are in themselves either endothermic or exothermic and so it is necessary within the system to provide for the addition of thermal energy to initiate the oxidation process and subsequently to control the system maximum temperature to ensure that the process does not exceed the design temperature of the plant. This temperature control is achieved by the utilisation of a combination of a heater and heat recuperative heat exchangers. Typically, the system will operate within a temperature range of 300 to 450°C.
Oxygen is used as the oxidant. A dedicated pressure swing adsorption system is utilised to generate a stream of low pressure oxygen from air. This oxygen is pressurised using a high-pressure compressor before the oxygen is metered into the reactor at the required addition rate to complete the reaction.
The AquaCritox plant is based on a tubular reactor, which offers many benefits over bubble type reactors including the elimination of back mixing and the ability to operate at higher than standard industry pressures. In turn this offers the potential to use higher process temperatures leading to greatly increased reaction rates and vastly reduced reactor retention times.
The plant is fully automated and is controlled by a plc-based control system equipped with full safety interlocks.
A liquid or slurry waste stream is transferred into the system feed tank. From here it is pumped into the system using a high-pressure feed pump which is chemically resistant to the expected feed type.
To start the system, the feed tank outlet valve is closed, and the process water valve is opened to allow water to flow to the suction side of the feed pump. The feed pump along with the choke water pumps are started and the system is allowed to reach system pressure.
Once system pressure is stabilised the process heater is started, and the system heats up to the pre-set process temperature. The feed pump forces the liquid through the primary process heat exchanger and through the heater circuit before entering the tubular reactor. Over a short time-period, the system reaches operating temperature.
Once operating temperature has been reached, a flow of oxygen into the reactor is initiated, and the water valve slowly closes off while the feed tank valve begins to open thus allowing the material in the feed tank to be fed into the system. The off-gas and reactor temperature are monitored. The control system ensures that the required amount of oxygen is always added to the reactor to ensure full oxidation.
While the system is in operation, thermal energy is recovered from the reactor effluent using a tube-in-tube type heat exchanger. The exchanger uses pressurised water on its annulus and transfers thermal energy from the reactor effluent to the incoming feed via the primary process heat exchanger, thus heating the feed.
Oxidation reactions are exothermic and so provided that sufficient thermal energy is available in the reactor effluent, it is then possible for the system to operate in auto-thermal mode.
After the reactor effluent has passed through the heat exchanger it is still under pressure. The flow passes through a cooler to bring the stream to ambient temperature and is then directed into the pressure control and let-down system where pressure is reduced from 240 bar to ambient. The pressure control and let down system is unique to SCFI and utilises a patented system of pressure reduction coils together with a choke arrangement. This system is particularly robust and capable of handling three phase flow which will always be encountered when processing waste streams such as sludges, slurries and contaminated waste waters and caustics.
A number of engineering solutions were needed to overcome process and safety challenges encountered in the development of this Eco-innovation supported demonstration plant.
While the process at overview level is simply described as pressurise, heat, add oxygen, cool down and depressurise, the detailed operation of the system is in fact much more complex.
As temperatures change within the system, the viscosity and density of water changes significantly. These process fluctuations can present problems in ensuring that solids will be transported through the system and so particular attention was paid to system velocities at each stage of the process.
Modelling ensured that effective solids transport was achieved by ensuring a minimum velocity based on density at each stage of the process.
Add your rating:
Current Rating: 2